How would you draw a 3-pos selector switch that turns on relay1 when it is in the left position, turns on a relay2 when it is in the middle ( neutral ) position and turns on relay3 when it is in the right position?
Turning on relay 1 and 3 is easy but I'm confused about how to turn on relay 2. I would need to put a NC contact at the right and left position of the SS and wire them in series. How would I represent this in a schematic?
I use some fairly commmon symbols that do this...
The filled square represents a closed position and come with the various positions filled.
Select the appropriate parent for the first contact and then the required contacts for all the other positions.
These blocks can be modified to use on 2, 4, 5, 6 or more position switches. Currently I have the 2, 3, 4 & 5 position blocks setup as I don't tend to use any more than that.
This stle of switch is also not limited in the number of contacts and positions that can be shown. Just keep adding the required contacts as needed.
This is how I have drawing the 3 position switch that is built from the AB selector switches. This would have two tiers of contact parts.
The first tier is made up of tweo N.O. Contacts.
The second Tier is made up of two N.C. Contacts. The first tier is for the left and right relay. The second tier is for the Middle relay. The terminal numbers are arbitrary to assign unique numbers for termination.
The selector switch symbols allow you to depict the switch position on the symbol (i.e., XOO,OXO, OOX) FOR LEFT , RIGHT , AND MIDDLE.
This is how I utilize the blocks I attached in my previous post....
As you can see I only use 3 contacts to operate the three relays and there is no confusion on what the contact position is when the switch is in it's various positions.
Start with some of our most frequented solutions to get help installing your software.
The AutoCAD Electrical forum has moved into it's very own category page, and can no longer be found within the Additional Product Forums.