I am attempting to connect a branch pipe (8" dia.) to a pipe main (10" dia.). I would prefer to have a weldolet connection to the main with the branch coming off of it. If a weldolet is not possible, can I "stub in" a branch without revit defaulting to putting in a full size tee, with a reducer on the branch section to the smaller diameter pipe?
If you wish to have a different type of default connection, you will, of course, need a Revit Family to represent it loaded into the Project. You can assign this Family as the default connection type for a specific Pipe Type. Either select a segment of that Pipe or find it in the Project Browser and go to Type Properties. Under "Routing Preferences", you can assign the default families for each Fitting Category.
Corey D. ────────────────────────────────────────────────────────────────────── ⁞|⁞ Please use .Accept as Solution and Give Kudos as appropriate to further enhance these forums. Thank you!