I have a 3 Phase 3 wire transformer with a 480v delta primary voltage. Is there anyway to circuit this up to the switch gear without a neutral wire? I have created a 480v Delta 3 wire distribution system in the electrical settings and assigned it to the transformer yet still it shows a 3 hot conductors and a neutral??
Did this ever get resolved? Seems to still be an issue (Revit MEP 2012). Revit doesn't give you the ability to edit the wire count (it's greyed out).
Log into access your profile, ask and answer questions, share ideas and more. Haven't signed up yet? Register
Start with some of our most frequented solutions to get help installing your software.