Revit Architecture

## Revit Architecture

Mentor
Posts: 219
Registered: ‎03-02-2013
Message 1 of 2 (121 Views)

# Thermal Cavity Materials - Forcing a Resistance to an air layer ?

121 Views, 1 Replies
01-20-2014 11:25 AM

I've run into problems with the in-Revit thermal calculations in the way that it handles cavities. I outlined them in an earlier post: Here.

I am still having problems - and haven't been able to come up with a workable work-around.

Essentially it boils down to the fact that Revit treats a cavity as a layer of air - and calculates its thermal resistance as a product of the thickness and conductivity of the air material - this means, by default that an air gap of 50mm provides the same insulation as 50mm of insulation rather than the (in the UK at least) recommended value of R=0.18 m2K/W. This skews the results considerably.

50mm unventilated cavity : R should be 0.18 m2K/W (0.44 m2K/W for low-e foil to insulation to cavity face)

50mm Revit air material : R = approx 2.0 m2K/W

As an example - the correct U-value for a given wall construction with a 50mm non-ventilated cavity was 0.268 W/m2K, Revit calculated it as 0.1935 W/m2K - nearly 30% lower than it should be (a significant deviation).

I had tried to get round it by assigning a 'fake' insulation value to the cavity's air material to ensure that the resistance for that layer comes out at the desired figure - the trouble is - as soon as someone changes the thickness of that layer, the result is incorrect again. Also, I would rather not assign an inaccurate conductivity to a material, you never know how/if it will be mis-used further down the line.

Is it possible to have a material provide a fixed Resistance - regardless of it's thermal conductivity or thickness ? (ideally with an allowance for the emissivity rating of the external face of insulation)

Apparently Revit includes the correct internal / external face heat transfer resistance (Rsi and Rs) - but not for a cavity (Ra.)

If I could create a material that has a pre-defined Resistance - I could create the appropriate fixed R rating as needed for walls, floors etc.

At the moment - it means that the U-Values generated by Revit only work accurately if there is no cavity present.

Anyone else encounter this problem ? If so, how did you get round it ?

Thanks,

Martin

Mentor
Posts: 219
Registered: ‎03-02-2013
Message 2 of 2 (73 Views)

# Re: Thermal Cavity Materials - Forcing a Resistance to an air layer ?

01-29-2014 04:52 AM in reply to: MKEllis

In case anyone else is searching, or has a similar query - Autodesk responded that they have passed the issue on to the development team, where it has been documented for possible resolution in a future version.

For the moment - I have created new materials - setup for specific cavity widths and named them as such: "Wall Cavity 50mm", " Wall Cavity 100mm" etc. and assigned the thermal conductivity as required to generate the specific R value (ie 0.18) at that specific width. It's not ideal - and is still subject to someone changing the cavity width and not changing the material - or vice-versa - but it is a work-around for the moment.

### You are not logged in.

Announcements
Are you interested in helping shape the Autodesk Community?
We’re looking at a few different ways to improve the “All Forums” landing page and need your feedback! If interested, please take a few minutes to fill out the following Usability Study. Thank you for your time!

### Maintenance Subscription Resources

Upgrading to a 2015 product? Make sure to check these out 1st!

### Revit Exchange Apps

Created by the community for the community, Autodesk Exchange Apps for Revit helps you achieve greater speed, accuracy, and automation from concept to manufacturing.